3150A 7.2 Kv Hv AC Vmd Vacuum Circuit Breaker with Assembly Pole
|FOB Unit Price:||US $1,560 US $1,280|
|Purchase Qty. (Pieces)||FOB Unit Price|
|Production Capacity:||22000PCS/Per Year Breaker|
|Transport Package:||Wooden Case Breaker|
|Payment Terms:||L/C, T/T, Western Union, Paypal|
- Model NO.: VMD
- Operation: Mannual & Electric Type Breaker
- Arc-extinguishing Medium: Vacuum
- Structure: Vcb Breaker
- Type: Circuit Breaker
- Certification: ISO9001-2000, CCC, Ohsas 180001
- Rated Current: 3150A Breaker
- mechanical Life: 10000times Breaker
- Trademark: Mingde Breaker
- Origin: Cixi, Ningbo Breaker
- Breaking Capacity: Middle& High Voltage Breaker
- Speed: Normal Type Circuit Breaker
- Installation: Fixed & Withdrawal Breaker
- Poles Number: 3
- Function: Overcurrent Protection
- Rated Voltage: 7.2kv Breaker
- Rrated Frequency: 50Hz Breaker
- Rated Short -Time Breaking Time: 20/21/25ka
- Specification: CE, SGS, TUV
- HS Code: 8535210000
The complete specification of VMD series vacuum circuit breaker can meet customers' different needs.It adopts the latest embedded poles and low-resistance vacuum interrupter and empolys an accurate gear driving system in the place of the traditional chain wheel driving system.
With main conductive circuit sealed in epoxy resin, the insulation performance will be more stable.VMD series circuit breaker has passed Type Test Report according to GB and IEC standards.It has exported to 26 countries and regions in the world.
|2||1 min power frequency withstand voltage||42|
|Lighting impulse withstand voltage(peak value)||75|
|5||Rated short time withstand current||KA||25,31.5|
|6||Rated withstand current(peak)||63,80|
|7||Rated short-circuit opening current||25,31.5|
|8||Rated short-circuit closing current||63,80|
|9||Rated duration of short-circuit||S||4|
|12||Average opening speed||m/s||1.1±0.2|
|13||Average closing speed||m/s||0.6±0.2|
|17||Rated operating order||O-0.3S-CO-180S-CO(<40KA)|
Normal Operating Environment Condition
a) Normal operating environment condition
Highest temperature: +40ºC
Lowest temperature: -15ºC
b) Environment humidity
Daily mean relative humidity: ≤95%
Monthly mean relative humidity: ≤90%
Daily mean saturated vapor pressure: ≤2.2×10-3 MPa
Monthly mean saturated vapor pressure: ≤1.8×10-3 MPa
c) Altitude: below 1000m area;
d) Earthquake intensity: no more than 8 degree;
e) The product shall be away from weep, fire and explosion, chemical corrosion and
strenuous vibration place.
Special Operating Condition
Please consult with manufacturer on manufacturing technology when operating environment is the climatic environment with high altitude, high humidity and great temperature change or other special environment condition.
(1) Circuit breaker should be in the state of opening and energy storage spring in a state without energy storage when packing. It should be in the state of opening and energy storage spring in a state without energy storage when packing. And it should be fixed on the bottom of the wooden case, should have waterproof measures and complete package labels.
(2) Circuit breakers can't invert and avoid strong vibration, rain, surface damage, and components lost when transportation.
(3) When loading the circuit breaker, we suggest the following tools: crane, forklift and driving. When lifting the circuit breaker, we should not hook on the body or pole of the circuit breaker, but on the lifting hole which has the lifting mark.
(4) When circuit breaker has a long-term storage, it should be in a state of opening and energy storage spring in a state without energy storage and placed in dry ventilated indoor preventing from moisture, vibration control and harmful gas erosion, and regularly checked whether environment meets the requirements.
(5)When first use products after long-term storage, it need to have a power frequency withstand voltage insulation testing.